Hardness Control 20 Kgs manufacturer supplier distributor in Mumbai, Kandla, Kolkata, Vizag, Chennai, India, Fujairah, Dubai UAE, Muscat Oman, Kenya Africa. Get the best quality of Hardness Control 20 Kgs at a competitive price from us. We have ready stock of Hardness Control 20 Kgs in India, UAE Gulf, Oman, Kenya Africa. Contact us for bulk as well as small orders.
Hardness Control is a white dry powder Phosphate Boiler Water Treatment product used for the reduction of hardness in boilers. Hardness Control is highly soluble in water and It will precipitate calcium hardness as a non-adherent sludge.
A precipitant designed to elimate scale deposits and lower the hardness of water in boilers with working pressure up to 60 bars.
It is used in conjunction with alkaline liquid to prevent calcium scale deposits. Both products are used in our standard boiler water treatment programs for low-pressure boiler systems (0-32 bar) and medium-pressure steam propulsion vessels (32-60 bar).
Benefit and Features
- Highly active phosphate based compound, economical in use.
- Easily dissolved in water for dosing.
- Scale problems due to calcium are eliminated.
- Maintains sludge in a non-adherent state for ease of blow down.
- Simple test to determine level of treatment.
- Can be used for boilers of all pressures.
Rxsol Hardness Control does not influence the alkalinity in the system
Sampling And Testing
A sample of boiler water should be drawn for analysis daily. The sample should always be taken from the same point after blow down, cooled and tested immediately. Follow the Rxsol Hardness Test Kit instructions and fill the Boiler Water Log Form according to result results. It is important that regular testing is carried out to ensure levels of treatment are correct.
Physical Properties :
Appearance :White powder
Corrosive action : non
pH 1% solution : 8,8
Flash point : none
Hardness Control is formulated to form a precipitate with calcium ions which will not adhere to metal surfaces but are in a form suitable for blowdown.
Used for boilers and water softening.
For optimum results dose Hardness Control direct to the boiler via the bypass pot-feeder. The dry powder should be dissolved in hot water (50°C) at a ratio of 1 part powder to twenty parts condensate (e.g. 500 grams/10 litres). Ensure that treatment is fully dissolved before dosing.
This treatment dosed at 1.49 grams per ton of distilled water provides 1.0 ppm phosphate.
Feed Points: Dose with other BOILER CHEMICAL / alkaline liquid by diluting withcondensate and feed directly into the system drum (below the water level) using a bypass pot feeder. For low-pressure boilers, It may be dosed to the hotwell or condensate return tank, although this is not the preferred method.
Dosage and control
Phophate test result in pPM PO4
0 - 10
10 - 20
20 - 30
30 - 40
40 - 50
> 60 Bar
> 880 PSI
Select row on righthand side for applicable pressure range. Compare test result with comment in table and dose stated amount of product per ton boiler water volume.
These are recommended values based on experience and are in no way intended to replace the boiler manufacturer's specifications or company regulations.